Hi. Appreciate any help. Goodman gas furnace/handler with separate AC compressor. Heat and AC worked fine last summer before the install. Installed in winter and heat works fine. Air handler circulates air in cooling mode but compressor doesn’t turn on at all (including after cleaning it out and changing fuses). Believe it is wiring problem.
Compressor is “Perfect Star” brand PA10JA042000ADAA. Furnace/handler is Goodman GDS80904BXCA.
Forum not letting me attach more than one photo, so here is original thermostat wiring (which worked):
From other photos:
At Wyze thermostat, i have connected wires Y1, W1, Rc, and C (labelled as such before disconnecting from original thermostat per guide). In comparing wire colors, looks like the wire that connected to G in the old thermostat is now labelled C and connects at C in Wyze thermostat.
At adapter, i have connected R, G, W, Y (C not connected)
At handler, I have connected Y, W, R, G, C from the adapter (no other ports on the board)
There is a sticker on a bundle of wires at handler(?placed on install?) on the wires at the handler stating
blue = c
green = g
white = w1
brown = w2
purple = y1
red = r
yellow = y2