I’m a little confused after watching the Wyze thermostat installation video, it states that no jumpers are required. My old thermostat jumps RC and RH. If RC stands for cold and RH stands for hot, which terminal do I connect the wire being jumped on the Wyze terminal block for AC and Heat?
Rc is internally connected to the heat outputs when it calls for heat unless you have something connected to Rh. Just connect it to Rc if you have a jumper to Rh.
Thanks I’ll try that!