Setup my Wyze Thermostat over the winter. I thought during the testing my A/C compressor kicked on but I may have been mistaken. Now that it is warming up it is not kicking on. I took pictures but it was hard to get a great angle.
Original Setup at furnace: Green > G White (from compressor) > Com 24V White > W Yellow > Y/Y2 Red(from compressor) > Y/Y2 Red > R
New Setup at furnace: G > G C > Com 24V White(from compressor) > Com 24V W > W Y > Y/Y2 R > R
C-Wire adapter: Green > G Red> R White> W Yellow > Y Red(from compressor) > Y
Please let me know what I did wrong.